System 200 Installation Advice
Hook-On Tiles, Concealed Grid
NotesEmac hangers should be installed a maximum of 300mm from the end of a run of Emac channel and 300mm from the joint between these channels. Where two J-bars meet and are spliced together, an Emac channel should be installed within 300mm.
For planks longer than 2000mm, the distance between Emac channels should be reduced to 1000mm max.
It is considered good practice to stagger joints in supporting structures.
Additional LoadsWhen supporting services such as downlights, speakers, detectors and other mechanical and electrical services, the maximum load applied to the ceiling tile must not exceed 7kg including spreader yokes if applicable. The application of a load should always be considered. Please consult the SAS Technical Department for further advice.
For loading for flange formed reinforced apertures, please consult with the SAS technical department.